LOT Manifold is installed where peak load of Equipments is higher & everage consumption of LPG is up no much ie its up to 2 tone per day. We called this is a small bullet. It can install instead of bulk where there is space no space for bulk installation. This system is completely safe to handle. We follow Is-6044 Part-1 & 2 & OISD norms for these types of installations.
A Gas Storage Facility consisting of multi-cylinder installation with Liquid off-tek Valve fitted on the cylinder which contains a stem pipe inside the cylinder so the liquid is drawn directly with inbuilt cylinder pressure every cylinder is fitted with Excess flow check Valve to ensure safety when any pigtail is burst or damage.
Cylinder Manifold: Consists of C.S Pipe Sch 80, 40NB pipe each arm consists of Smart hose with inbuilt NRV & isolation valve to restrict liquid from leakage.
The liquid is drawn directly from the cylinders which passes through the electrically / steam operated Vaporizer to give us required Gas i.e. vapor.
Pressure Reducing Station: Regulators are selected and installed to reduce the required pressure as per the requirements.
Safety Relief Valve is provided as an additional safety factor.
A Excess flow check valve is installed on each manifold to ensure safety when any down stream line is breakage or damage.